Projects per year
The test method of the standard EN12975-2 (European Committee for Standardization, 2004) is used by European test laboratories to determine the efficiency of solar collectors. In the test methods the mean solar collector fluid temperature in the solar collector, Tm is determined by the approximated equation where Tin is the inlet temperature to the collector and Tout is the outlet temperature from the collector. The specific heat of the solar collector fluid is in the test method as an approximation determined as a constant equal to the specific heat of the solar collector fluid at the temperature Tm. The power produced by the solar collector during a test period is determined by the product of the specific heat, the mass flow rate and the temperature increase of the solar collector fluid. The solar collector efficiency is in the standard determined by measurements at different temperature levels. Based on these efficiencies, an efficiency equation is determined by regression analysis. In the test method, there are no requirements on the ambient air temperature and the sky temperature. The paper will present an evaluation of the test method for a 12.5 m² flat plate solar collector panel from Arcon Solvarme A/S. The solar collector panel investigated has 16 parallel connected horizontal absorber fins. CFD (Computational Fluid Dynamics) simulations, calculations with a solar collector simulation program SOLEFF (Rasmussen and Svendsen, 1996) and thermal experiments are carried out in the investigation. The investigations elucidate: • How the mean solar collector fluid temperature Tm is underestimated by the approximated equation in the test standard and how the collector efficiency equation is influenced by the underestimation of Tm. The dependence of the volume flow rate is shown; • How the use of the approximated specific heat of the solar collector fluid is influencing the collector efficiency expression; • How the temperature levels used is influencing the collector efficiency expression; • How the measured collector efficiency is influenced by the weather conditions such as the ambient air temperature and the sky temperature. Based on the investigations, recommendations for change of the test methods and test conditions are considered. The investigations are carried out within the NEGST (New Generation of Solar Thermal Systems) project financed by EU.
|Publication status||Published - 2006|
|Event||Euro Sun 2006 : IESE-Europe Solar Congress - Glasgow, UK|
Duration: 1 Jan 2006 → …
|Conference||Euro Sun 2006 : IESE-Europe Solar Congress|
|Period||01/01/2006 → …|
FingerprintDive into the research topics of 'Evaluation of Test Method for Solar Collector Efficiency'. Together they form a unique fingerprint.
- 2 Finished
22/04/2004 → 31/12/2005