This is a report of the results of phasor measurement unit (PMU) laboratory development and testing done at the Centre for Electric Technology (CET), Technical University of Denmark (DTU). Analysis of the PMU performance first required the development of tools to convert the DTU PMU data into IEEE standard, and the validation is done for the DTU-PMU via a validated commercial PMU. The commercial PMU has been tested from the authors' previous efforts, where the response can be expected to follow known patterns and provide confirmation about the test system to confirm the design and settings. In a nutshell, having 2 PMUs that observe same signals provides validation of the operation and flags questionable results with more certainty. Moreover, the performance and accuracy of the DTU-PMU is tested acquiring good and precise results, when compared with a commercial phasor measurement device, PMU-1.
|Title of host publication||2010 IEEE PES : Innovative Smart Grid Technologies Conference Europe (ISGT Europe)|
|Publication status||Published - 2010|
|Event||1st IEEE PES Conference on Innovative Smart Grid Technologies Europe - Lindholmen Science Park, Gothenburg, Sweden|
Duration: 11 Oct 2010 → 13 Oct 2010
Conference number: 1
|Conference||1st IEEE PES Conference on Innovative Smart Grid Technologies Europe|
|Location||Lindholmen Science Park|
|Period||11/10/2010 → 13/10/2010|
Bibliographical noteCopyright 2010 IEEE. Personal use of this material is permitted. However, permission to reprint/republish this material for advertising or promotional purposes or for creating new collective works for resale or redistribution to servers or lists, or to reuse any copyrighted component of this work in other works must be obtained from the IEEE.
- Universal coordinated time (UTC)
- Synchronised phasor
- IEEE C37.118
- Phasor measurement units